York Diamond 80 furnace (older I believe a 1995)
Posted 04 November 2006 - 04:40 PM
So, I noticed when this happens there was a red light blinking. I opened it up and found the code list. It was blinking 5 times and that listed the Rollout open, no call for heat. It sure makes sense but can anyone give me direction on what can be causing this.
Thanks in advance,
Posted 04 November 2006 - 06:32 PM
Most intermittent ignition problems are due to weak flame signals. I would start by cleaning the flame sensor, (it is the metal rod usually in front of the left most burner, opposite of the ignitor) - pull it out and clean the rod up with very fine sand cloth or steel wool. Also check the condition of the burners, hitting the front of them with a wire brush will do them good.
Posted 16 November 2006 - 06:05 AM
-old Irish saying
Buy me a beer through paypal: firstname.lastname@example.org
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users