Gibson Fridge Trips Breaker
Posted 25 September 2005 - 06:53 PM
After cycling it 10 times, I set the defrost timer to a position just past the defrost cycle. The unit ran for about an hour and was cool. I manually cycled the defrost timer and the unit did not trip the breaker when the defrost cycle was reached.
Anyone have an idea as to why it was tripping the breaker and now is not?
Posted 25 September 2005 - 07:40 PM
Just curious as to why it tripped sometimes and not others when the timer hit the defrost cycle.
Posted 26 September 2005 - 05:37 PM
Weak GFCI breaker. Try an extension cord to another circuit and test.
I just installed a new 20A GFCI. Frige trips the new GFCI. Test a non-GFCI circuit and it fridge did not trip it.
What is causing the frige to trip the GFCI?
Posted 26 September 2005 - 07:25 PM
CLICK HERE TO BUY PARTS
Appliance Repair In Maryland http://serviceeveryday.com
Posted 27 September 2005 - 01:11 AM
Here's how you can verify this: Get one of those handy adapters that convert a 3prong grouded plug to a two prong plug, (Make sure the adapter that you use has the little ground lug that sticks out the side that can be screwed to the center socket screw.
Now, plug your power cord with the adapter on it into the GFIC plug, DO NOT hook up the ground lug. Now if you put the frig into defrost I can garantee you that it won't trip the GFIC or the circuit breaker in the fuse box.
Now to actually verify, you will need to use your meter and check for AC voltage from the ground lug adapter of the 3-prong plug adapter to the ground hole of the GFIC. I can almost assure you that you are going to be seeing a reading of a couple of volts. This leaking voltage to ground is tripping the GFIC -- It's a ground fault.
Now, go find where the leakage is occuring ----- GOOD LUCK.....
Willie's Budget Appliance Repair
Eureka, CA 95501
Posted 27 September 2005 - 05:09 AM
I read this on a few sites after a quick google. Also, when I plugged the frige into a non-GCIC outlet, it never tripped a circuit breaker in the fuse box.
It is my understanding Refrigerators are not to be run on these anyway, best to plug into a regular outlet.
If there is no voltage on the ground, I will probably convert the outlet to a standard outlet or run a dedicated circuit.
Thanks to all that have helped out.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users