Lennox diplomat 80MGF blower works for heat but not a/c
Posted 08 May 2011 - 07:58 PM
Posted 08 May 2011 - 08:28 PM
Note that when "W’ is energized, the blower is delayed 45 seconds.
If there is 120V to each motor tap but the blower does not operate, replace the motor.
If there is not 120V at the Motor when "Y", "G", or "W" is energized, replace the control.
For service manuals and lots of other goodies,
become an Apprentice==> http://appliantology.org/apprentice/
one of my video productions: “Easter Seals: Walk With Me”
every day is Down Syndrome Awareness Day
"A Child Is Waiting" . Burt Lancaster . Judy Garland . 1962
RegUS_PatOff > www.youtube.com/watch?v=oPAY2LsKVEw
Posted 09 May 2011 - 11:43 AM
Electric heat uses one speed wide open.
So a way to switch speeds from low speed fan for gas heat to hi speed fan for air conditioning is done by use of a fan relay.
Older units use a relay, newer units use pc boards. Just thought I would throw that in.
"May the hinges of our friendship never grow rusty"
-old Irish saying
Buy me a Beer: http://web.me.com/ze...man18007260692/
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users