Posted 26 July 2011 - 01:51 PM
Posted 26 July 2011 - 02:04 PM
Edited by applianceman18007260692, 26 July 2011 - 02:05 PM.
"May the hinges of our friendship never grow rusty"
-old Irish saying
Buy me a Beer: http://web.me.com/ze...man18007260692/
Posted 26 July 2011 - 02:13 PM
Posted 26 July 2011 - 05:37 PM
disconnect the 2 wire at the furnace and at the condenser leave them hanging in the air. Take an OHM reading between the 2 wires . you should get no resisatance of any kind . then check each wire to a good ground. again you should get nothing . Tie one end of the wires together. take a reading . it should be very low resistance (less than 10) .
If those check out then the problem is in the condenser most likely.
Check for resistance to ground on the wires going into the condenser control circuit . there should be none.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users