Amana guia090a30 continuos flash codeflame senced 5 sec with out
Posted 20 October 2011 - 10:17 PM
flame senced >5 sec without gas valve.
igniter lights up, flame turns on for about 2 sec. then it restarts about 3 time, then blower runs with out flame.
Need your help
Posted 20 October 2011 - 10:29 PM
If the control senses a flame when the gas valve is de-energized,
it will run the air circulator blower and the induced draft blower continuously.
The probable causes are either a short to ground in flame sense circuit,
miswiring, lingering burner flame or a slow closing gas valve.
Need parts? Call our Parts Department now! 877-803-7957
Posted 21 October 2011 - 01:07 AM
Thanks a bunch
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users