Bryant 1996 heat pump
Posted 03 May 2012 - 05:12 PM
Posted 04 May 2012 - 07:01 AM
First look closely at the capacitor.
Is it bulged on top?
Test the capacitor if you can get a cap tester.
Remove the start relay cover on the compressor and inspect the 3 wires for loose or burned wires.
Remove the compressor wires and ohm the compressor.
If the compressor checks OK,replace the wires then remove the fan motpr wires from the contactor.
Start the compressor.
If it starts OK with no noise,replace the fan motor.
Posted 04 May 2012 - 11:19 AM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users