Posted 29 May 2012 - 12:12 AM
Posted 29 May 2012 - 08:11 PM
edit: hopefully the two halves are for the same flavor refrigerant??
Edit 2: You will need to have somewhat of the required airflow through the blower/ductwork to match, but probably less than usual since the evap coil is so big. Just please warn whoever works on it down the road what has been done. Put a gigantic red sticker on it saying "beware" or something This sort of thing can make a service guy lose his mind trying to figure wtf is happening.
Edited by Bullstok, 29 May 2012 - 10:51 PM.
Posted 30 May 2012 - 01:12 AM
Posted 30 May 2012 - 01:19 AM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users