is installing split wallmount ac a DIY job?
Posted 25 August 2012 - 08:27 PM
Posted 29 November 2012 - 07:40 PM
1) Stay away from Chinese mini-split systems sold online with names you don't recognize!! It's all crap! I've seen too many DIYers order that garbage and then want me to try and fix them.
DIY install isn't too bad if you read the instructions. You'll need someone with a vacuum pump to leak test and pull a vac. Buy youself a lineset with the flare fittings already on the ends. If it's a little long don't cut it just loop the extra behind the unit. If your linset is 25' or less you just pull a vac, open the service valves and walk away. No need to fine-tune the charge. I'd stay away from LG; too many bad thermisters and crappy tech support. Online manuals and troubleshooting guides are grossly outdated.
I love Fujitsu. Solid and well-built. If I have a pre-sale question or a service issue I call their 800 number, leave my name and number with the receptionist and I have a tech engineer calling me back in less than 20 minutes.
- Samurai Appliance Repair Man and RussTech like this
Posted 19 December 2012 - 01:32 AM
Second that. Fujitsu is the best built, best value in the industry.Have installed MANY. not a single clinker in the bunch. Shootist speaks the truth re: vacuum and charge, I triple evacuate always. Nitrogen leak test between vacs, 400 microns or better.
- Samurai Appliance Repair Man and kdog like this
Posted 18 April 2013 - 01:07 AM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users