Ya know, I checked the terminal cord to 240 receptical Had a loose connection there. Got it where I have a steady 120 each leg & 240 across each terminal. Followed with continuity checks at fuse & thermostat. Full song. Continuity check at heat element, sings well on meter. No continuity from element to housing. Pulled element & inspected it looks fine.
Not having a tech, I tested for voltage drop at al fuses & therms. 0 volts across terminals & 120v from each terminal to ground. Heater elements 120v to ground & 0 v across terminals. Should I not have 240 across the heater elements with motor running. Pulled terminals off heater element & I have 120v from each to ground, 0v across red element wires. Trying to remember voltage from timer terminals to ground. Anyway I suspect timer issue.
Correct me if I'm wrong in my thinking. I still stumble in Elec 101.