Goodman 100k BTU Forced Air Furnace(Wont stop running)
Posted 19 February 2006 - 12:06 PM
Model #GMP100-3 REV B
It has been rather cold here this weekend and the furnace wont quit running and will not raise the temp just hold it steady at about 63-65 degrees. It seems like most of the heat is getting vented up the chimney vent(that duct is the hottest) and the fire doesn't run for very long. About 1-2 minutes every time. I was wondering if this is something I might be able to fix or if I should just call the repair man tomarrow. Seems like it resets it self to often.
Thank you very much!
BTW- I have all new vinyl windows and only a VERY small draft in one door. THis is my first year in this house and I dont know if this is normal or not. Sure doesn't seem like it.
Posted 20 February 2006 - 12:16 AM
Posted 20 February 2006 - 04:55 AM
Posted 20 February 2006 - 05:08 AM
If so find the wiring diagram and locate the high limit safety
switch and by-pass it with a jumper. If the switch is bad the gas will stay on. If the switch is bad replace it. Do not operate the furnace with it jumpered out you could start a fire.
Posted 20 February 2006 - 05:30 AM
Posted 20 February 2006 - 09:20 AM
Seems to be working great now. has went up 4 degrees in 1 hour(best ever since I lived here).
Thanks again for your help and I really appreciate this web site and will refer anyone to it if they have any problems it's really helpfully to have someone that knows what they are dealing with.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users