AC not cool enough and thermostat not working properly
Posted 07 July 2006 - 09:58 AM
Posted 08 July 2006 - 08:45 AM
Posted 08 July 2006 - 10:16 AM
Going back to the basics. Have you checked your air filter? If you check the return and the supply air temp at the furnace you should have 18-22 degrees difference.
The HVAC in the house where I live is probably typical of most. There is a return air grate covering the filter leading to the plenum, from which the air is drawn to go through the condenser/heat exchanger. The unit is a combo heating and cooling with the condenser sitting on top tightly sealed with aluminum tape, etc.
Where and how can the temps you refer to be read? I have a thermometer with a 4 inch probe on it.
Thanks for your help.
Posted 08 July 2006 - 05:51 PM
Posted 13 July 2006 - 06:39 PM
"May the hinges of our friendship never grow rusty"
-old Irish saying
Buy me a beer through paypal: firstname.lastname@example.org
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users