AC Advive please
Posted 12 August 2006 - 05:46 PM
It's been running again for about an hour now. Is it something I can fix, or do I need to call in for repair. Sorry for so much detail, but wanted to explain fully.
Any advice / help would be appreciated.
Posted 13 August 2006 - 03:40 AM
I sounds like your condenser fan motor is bad. It may have been caused by a bad run capacitor. General replacement motors go for around 70 bucks, but spend the extra $5 for the capacitor. It's probably a 1/3 or 1/4 horsepower 230 volt motor. If you decide to attack the job I can help you through it.
"The answer is that.......wait...what was the question again?"
Posted 13 August 2006 - 03:48 PM
It's been on all day, but I know it's only a matter of time. I'm going to look into getting the parts, and would really like to switch it myself. Doesn't "sound" incredibly hard, but I'm a novice. I would appreciate your advice / guidance, if I go forward.
And welcome to the forum also.
Also, thanx Applianceman,
your and ahammer's previous advice to others is what decided it, for me to join.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users